API 653 TANK INSPECTION,TANK MAINTENANCE,ANDCAUSES OF TANK FAILURE
API 653 Tank InspectionsWhy Inspect Your Tanks? Prevent leaks into your secondary containment or togroundwater (if you do not have a secondary containmentsystem) Establish a baseline of tank condition and corrosion rates Identify problems to perform repairs before you have asignificant leak or release - Maintain your capital asset Minimize chance of catastrophic tank failure
PROPER INSPECTION PROTOCOLINSPECTOR CREDENTIALS Certified API 653 Inspector Four years minimum experience with storage tanks Must pass test conducted by American Petroleum Institute (API) Inspectors receive an individual inspector number Inspector testing required every three years
PROPER INSPECTION PROTOCOL Visual inspection of welds, plates, and appurtenances UT (Ultra-sonic Thickness) testing of shell courses, floor, and roof Vacuum testing of all floor weld seams – unless epoxy coated Identify bottom side corrosion on floors Settlement Survey Checking for planar tilt Check for floor bulges or depressions Provide calculations for safe or maximum fill height
Weld deteriorationPlate corrosion
Interior piping corrosionShell corrosion
Weld deterioration andfour-way junction – NON APIFour-corner insert withreinforcing backup – NON API
Evidence of interior shell corrosionFoundation evaluation
Floor plate corrosionLap-welded seam leak
Floor coupon with bottomside corrosionFloor top side corrosion
Severe roof corrosionStar light . . . Star bright!
TANK INSPECTIONS ARE NOT ALWAYS A BAD THINGTHIS IS A HAPPY TANK
TANK MAINTENANCE – COMMON SENSE APPROACH Conduct monthly/weekly walk-around of your tank(s) Look for stains on steel where leak may be occurring Check valve function and nozzle welds Check associated piping Check foundation for wash-out/deterioration Keep good records of product in and out
TANK MAINTENANCE – COMMON SENSE APPROACH Open up your tank a minimum of every two years and conduct yourown visual inspection inside Check for weld deterioration and corrosion If tank is coated, visually check coating for blisters or cracks Keep a record of inspections and results If tank has an internal containment liner, check leak monitor weekly Conduct an API-653 inspection of your tank every five years asrecommended by TFI (The Fertilizer Institute)
WHAT IS THE API 650 SPECIFICATIONAPI - AMERICAN PETROLEUM INSTITUTEWorldwide Standard for Above Ground Storage Tank Design andConstruction Provides requirements for calculations of shell plate thickness,man-way and nozzle design Provides procedures for shell, roof and floor construction Specifies material requirements and minimum thicknessrequirements Specifies weld construction requirements, weld spacing, andx-ray requirements
CAUSES OFCATASTROPHICTANK FAILURE
TANK FAILURES – COMMON CAUSES Tank shell plates not thick enough for specific gravity of productstored Over-filling of tank – over pressure Cut-down and re-erected tanks using improper cutting andre-welding procedures Improper weld procedures Lack of full weld penetrations (lack of weld fusion) Improper weld seam spacing Lack of radiograph (x-ray) of newly constructed tanks or onrepaired tanks
TANK FAILURES – COMMON CAUSES Lack of weld fusion - #1 common cause Welders not certified and tested to weld procedure Weld deterioration/corrosion – especially in lower horizontal andvertical weld seams Brittle fracture of steel Lack of proper certified inspections Tank erectors who know little about API Specifications andprocedures – these companies attract customers with a “cheap”price. Make certain your contractor can verify that your tankmeets API Specifications. DO YOUR OWN HOMEWORK
Cut-down and re-welded tankImproper weld spacing
Double wall 500,000 gallontank, Illinois 2008Cause – overfilling and lack offusion on weld seams
Yards of destruction
Original tank foundation
Weld seam rupture. Force of rupture “pushesback”. Rupture on side of camera location.
Conduct an API-653 inspection of your tank every five years as recommended by TFI (The Fertilizer Institute) WHAT IS THE API 650 SPECIFICATION API - AMERICAN PETROLEUM INSTITUTE Worldwide Standard for Above Ground Storage Tank Design and Construction Provides requirements for calculations of shell plate thickness, man-way and nozzle design Provides procedures for shell, roof and floor .
API 653 only applies to tanks that have been built and placed in service (see 1.1.1). Therefore, the tank will need to comply with all of the requirements of API 650. 1.5 2nd - Dec. 1995 653-I-04/99 Does API 653 require contractors performing repairs to have a API 653 certified inspector employed with them, and if so, where can this be found in
5.5 API 653: inspection intervals: practice questions 77 Chapter 6: Evaluation of Corroded Tanks 6.1 Introduction 80 6.2 The contents of API 653 section 4: suitability for service 83 6.3 Tank roof evaluation 83 6.4 Shell evaluation 85 6.5 API 653 (4.4): tank bottom evaluation 98 6.6 Foundation evaluation: API 653 (4.5) 105 6.7 Bottom settlement .
(API-653, Paragraph 9.14) b) The inspector should be able to calculate the minimum spacing between an existing nozzle and a new hot tap nozzle. (API-653 Paragraph 9.14.3) 6. SETTLEMENT EVALUATION The Inspector should be able to calculate the maximum allowed settlement for the following: a) Edge Settlement (API-653 Annex B.2.3, fig. B-5)
S. Saxbury (API-653 #50761), A. Majors and S. Barrows . Reviewed By . Terry Wach PE, API-653 #50849 . API-653 INTERNAL TANK INSPECTION EVALUATION Tank No: 2 September 23, 2015 Chouteau, OK Grand River Dam Authority TC9338 . This document is intended for the so
The ARINC 653 standard ARINC 653 Specification First Published Jan 1997 ARINC 653 Supplement 1 Oct 2003 – Provided refinement and clarification to the 1997 standard ARINC 653 Part 1 (Required Services) Supplement 2 Mar 2006 – ARINC 653 partition management – Cold s
API 575 Study Guide API 653 Cert Prep MSTS 1 Sept 2021 This Study Guide has questions to help you learn the content of API RP-575, Inspection of Atmospheric and Low-Pressure Storage Tanks (4th Edition-2020). On the API 653 exam, there are about 8-12 questions from this document. We do NOT spend time in class discussing this publication. Why?
api 20 e rapid 20e api 20 ne api campy api nh api staph api 20 strep api coryne api listeriaapi 20 c aux api 20 a rapid id 32 a api 50 ch api 50 chb/e 50 chl reagents to be ordered. strips ref microorganisms suspension inoculum transfer medium i
14 Mercedes Benz A250 2014 Wheel alignment Wheel alignment specifications. Contacted VACC, no information available, checked online for OEM websites, blocked from USA and Europe. 15 Suzuki Jimny 2008 Collision repair Body repair quarter panel replacement procedures. Contacted VACC, no information available, checked online for OEM websites, blocked from USA and Europe. 16 LDV G10 2016 Service .